Read about START-PROF pipe stress analysis software

Let’s imagine the simple piping model – console pipe. Fixed Anchor on the left end and free end with sliding support at the right.

In installation state (a) at ambient temperature friction forced doesn’t exist because there’s no displacements. The fixed anchor load R is zero.

In operation state (b) pipe elongates and right end slide in right direction. Friction force is always directed in the opposite direction of movement. Therefore friction force direction is from right to left. The friction force value is F= µ *W, where W is support load from weight load, µ is friction factor. The fixed anchor load is R=F.

Will friction force and support load R exist in cold state (c) or not? The answer is yes! The right end of the pipe will slide to the left direction during cooling down. The friction force will change it’s direction to the right. When pipe will reach the ambient temperature friction force will not disappear. The fixed anchor load will be R=-F. The effect of friction forces in cold condition looks like cold spring effect. The pipe remains under tension, support loads are not zero.

This phenomena can also be illustrated using the heavy brick and spring. We push the brick in right direction (b) and then pull it back into left direction (c). The spring in cold condition (c) will renain stretched. Reaction force R will be not zero.

Should we consider this effect during pipe stress analysis calculations? Yes!

Usually, when engineers perform pipe stress analysis, the friction forces in cold state assumed to be zero. The following load cases can be created:

L1: W+P SUS

L2: W+P+T OPE

L3: L2-T COLD (follow up L2)

L4: L2-L1 EXP

L5: L2-L3 EXP

Usually we calculate expansion stress range L4 between operation condition (L2) and installation condition (L1). But what if we will calculate expansion stress range (L5) between operation condition (L2) and cold condition (L3)? Will it be greater or lower?

In operating condition L2 the stress due to friction is compressive S=-F/A.

In installation condition L1 the stress is zero S=0.

In cold condition L3 the stress is tensile S=+F/A.

This means that L4 expansion range will give SA=ABS(-F)/A=F/A, but L5 expansion range will give SA=ABS(-F+F)/A=2*F/A.

Expansion range L5 is 2 times greater than L4! It’s more correct to calculate expansion range between operation and cold state (L2-L3) with friction instead of operation state and installation state without friction (L2-L1).

Friction factor decrease after several movements. Thus sometimes friction factor for L5 stress range calculation is required to be decreased by 1/2 from full value. For example, if friction factor for L2 load case is µ =0.3, then for L3 we should use µ =0.3*0.5=0.15. In this case the stress range L5 will be SA=ABS(-F+0.5F)/A=1.5*F/A.

Let’s check how to calculate this in PASS/START-PROF software.

Create new simple model, pipe with fixed anchor in the left end and sliding support with a heavy valve on other end.

Modeling of the cold state with friction is a standard function of START-PROF operation mode editor.

If the option “Stress Rang from Operation to Cold” is turned off, START-PROF will calculate stress range L4 (between operation L2 and installation L1). If we turn on this option, START-PROF will calculate stress range L5 (between operation L2 and cold L3) considering backwards friction effect.

In the stress table we can see, that stress range is 2 times greater for stress range operation-cold L5 than for operation-installation L4.

Let’s compare support loads in Installation state L1 and Cold state L3. In installation state the support load in X direction is zero. But in cold state it is not zero and equal to friction force on sliding support.

In some cases the friction effect may give even greater nozzle loads in cold state than in hot state.

After second heating of the complex piping system the displacements will be slightly different from displacements during first heating up. The same situation with second, third, etc. cycles.

Let’s imagine that we have several heating and cooling cycles

L1: W+P SUS

L2: W+P+T OPE

L3: L2-T COLD (following up L2)

L4: L3+T OPE (following up L3)

L5: L2-T COLD (following up L4)

L6: L3+T OPE (following up L5)

L7: L2-T COLD (following up L6)

L8: L3+T OPE (following up L7)

…

For the L-shape piping model, the sliding support displacements diagram in XY plane has the following shape:

The greatest loads will be at first cycle L2-L3. The greatest stress range will be L2-L3. The L1-L2 range is not greatest.